Notes on operation and installation
Planning by Dialock specialist is required.
DT 710 door terminal modules on fire resistant and smoke control doors must be installed by Dialock specialists after approval by the door manufacturer. Otherwise the Fire and Smoke Control Certificate for the door will be invalidated.
Only to be used in combination with DIN mortice lock for DT 710. The comfort function is set via the mortice lock.
If an escape route door in accordance with EN 179 is required, only door terminals with U-shaped lever handle aperture parts are permitted.
Mechanical emergency opening
The DT 710 door terminal set must always be equipped with a profile cylinder to make mechanical emergency opening possible. The installation of a profile cylinder with fire resistance approval is mandatory for approval as a fire resistant or smoke control door. When using mechanical emergency opening, please note the information sheet for determining the length of the single profile cylinder.
The batteries in the door backplate interior module are secured in the covering with a special screw. This is intended to prevent unauthorised battery removal. For this reason, a special bit is required to equip the interior module with batteries, which must be ordered separately.